Find great deals for Andover Controls Continuum NetController LL Cx Tac Inc.. Shop with confidence on eBay!. Andover Continuum™. Product Catalogue. Issue: October . Infinet NetController II CPU Module. Infinet NetController – Display Modules. NetController II Andover Continuum power supply or third-party UL Listed UL Be sure your Andover Continuum cabinet is connected to the ground.
|Published (Last):||10 May 2007|
|PDF File Size:||6.47 Mb|
|ePub File Size:||8.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
Andover Controls Net controller problem
One last thing, check to see if all the programs and functions are correct and match the text file. Valves, Regulators, Filters, Etc. Do a “send to controller”. But I woul netcontrollef to try them. Next create a new network controller, do a teach.
But at a stage when I send blank controller to SQL database, in the distributions window i netcontrolller error produced: Version of Continuum is 1. I usually remark the error lines out until I a clean import.
I could see my controllers online. I’ve seen this problem before. Sorry, one more question, how to send data to controller from text file?
Andover Controls Continuum NetController LL Cx Tac Inc. | eBay
I am very sorry, I’m not very good at English. This should reset the controller, wait for it to come back online, then send the system variables to the controller.
Thanks you Very much.
This is not a DIY andovr and what I suggested is not for the faint of heart. I haven’t done what Autopilot has discribed. I hope you can help me solve this problem. If we evolve from the monkey then why are there still monkeys. Even i tried to delete nw and everything which i have created. Building Success with Routines and Rituals. I’m asking this question because I haven’t done it.
Andover Continuum NetController II – Feature Blast
I have been unable to find the cause for the SQL database corruption. Related Forums The place where Electrical professionals meet. After a successful import no errors you should be able to reload the controller without any problems. If controller is functioning properly it should come back online totally blank.
After creation of network I learn controllers. If all is good at this point your controller is good. Oil Burners Pro’s Forum: Thread Tools Show Printable Version.
Building Science Discussions Pro’s Forum: I think that this is also database problem, because i think controller work in “NoDB” mode, but may be i wrong.
If all is well, the controller will be ready to reconcile any handle issues it the text dump. Note the values of the errors and freemem system variables. Power Quality Pro’s Forum: If you get any errors during the text import, you will need to correct them.
The time now is First question is what version of Continuum are you using? Like Borias we sometime encounter the same problem. I have done some reloading, created points, revise the program but not this deep of situation If we evolve from the monkey then why are there still monkeys. Results 1 to 10 of First you have to go to the Menu bar forgot the term at the bottom right and find the controller ICON.
Then One Foggy Service Call All three controllers are online and reply for ‘who is’ global broadcast. It’s rare, difficult and time consuming to trouble shoot. It takes around half an hour to learn. Go back online and do a explorer refresh. I only do this on controllers that have the problem Borias described.
Borias, From your question about saving a text file I’m wondering if you have had any formal Continuum Training. All times are GMT Set send to controller options to metcontroller attached objects, but not attached controllers”. When you reload the controller, the proper path, and handle info is sent to the controller.